Type of Pool:
Leakalyzer, Pressure Testing Equipment, XLT30H, Hydrophone, Dye
Customer reported that the pool was leaking 1-2 inches per day and that a new liner was installed recently. When we arrived, the pool level had already dropped below the skimmers and returns.
We ran a pump on and pump off test with the Leakalyzer and found the pool was losing slightly more water with the pump off. This indicated that we should suspect suction side plumbing. Since the pool water level was already below the skimmers we dove down to check the main drains. A dye test confirmed that the main drain line was drawing dye from both of the two main drains.
We set up our pressure testing equipment to start pinpointing the location of the leak and ran a quick pressure test with water first to confirm that what the dye was showing was accurate. Once we started inducing air and purged all the water from the line we were able to hear a good leak noise in two spots with the Hydrophone (attached to the XLT30H). The first noise was right at one of the main drain bowls and the other was in a corner of the pool. While we had the main drain lines plugged we also ran another Leakalyzer test, which verified the water loss had stopped in the pool so there was no need to run a LeakTrac on the liner or dye test the fittings, skimmers, etc.
In order to determine which noise we were hearing was actually the leak, we slid an inflatable plug 8’ into the line from the main drain bowl and re-pressure tested. The pressure test still failed, so we knew the leak had to be farther than 8’ away from the main drain bowl. With this information we decided that the place we heard noise in the corner of the pool was the leak location. Another confirming factor was that while we were inducing air, there would occasionally be a bubble that came up behind the liner to the surface of the pool. Before leaving we also ran pressure tests on skimmer and returns to verify the rest of the plumbing was good.
- Pressure testing helped us identify actual problem when the noise was heard in multiple locations.
- Leakalyzer verified that pool shell was leak free, saving us time during the isolation phase.